A simplified method to calculate the light level in a room.

In lighting design, the lumen method, (also called zonal cavity method), is a simplified method to calculate the light level in a room. The method is a series of calculations that use horizontal illuminance criteria to establish a uniform luminaire layout in a space. In its simplest form, the lumen method is merely the total number of lumens available in a room divided by the area of the room. In order to perform this calculation, many factors, coefficients, lamp lumen data, and other quantities must be gathered. Despite the scientific impression of the lumen method equations, there are inaccuracies and assumptions built into the method. Therefore, the lumen method should not typically be used as a standalone, final solution; it should be used as a tool in particularly uniform settings of lighting design if a simple, rough technique of illuminance quantification is desired.

A step-by-step guide is given in textbooks and the IESNA Lighting Handbook.

The lumen method, in brief, consists of a calculation of the "cavity ratios" of the upper, middle, and lower volumes of the space to be lighted. The lower cavity is from the floor to the working height, the upper cavity is from the lower edge of the luminaires to the ceiling, and the middle cavity is the volume between these planes.

The effective reflectance of ceiling, floor, and walls are estimated from tabular data. A coefficient of utilization, representing the fraction of light that is directed to the working plane, is supplied by manufacturers for each luminaire design for the various calculated room cavity ratios.

Some of the light produced by the lamps is lost due to non-ideal lamp operating conditions, dirt on the luminaires, dirt on the room surfaces. A light loss factor is calculated for all these, based on tabulated empirical factors.

Given the usual lighting problem of obtaining an average lighting level at the working plane, the number of luminaires can be calculated based on the effective amount of useful light that each luminaire has been calculated to emit.

Since the zonal cavity method only gives an average lighting level, manufacturers tabulate recommended spacing to mounting height ratios that must not be exceeded if uniform illumination is desired.

The lumen method can be manipulated to solve for a particular variable. This is valuable because certain numbers are needed at different times in the design process. “Number of luminaires” is important because this number can be used to estimate costs and layout the spacing of luminaires in a computer lighting calculation program (Steffy 2002).

calculation

design

floor

lumen

lumen method

luminaires

method

room

space

zonal cavity method

design

floor

lumen

lumen method

luminaires

method

room

space

zonal cavity method

Total flux method

Zonal cavity method

No comment found.

Videocide.com is service provided by Codecide, a company located in Chicago, IL USA.